Schneider Electric Singapore Website×
When the Neutral CT is not connected, the Earth Fault protection still operates in Micrologic 6.0 trip unit as it works on the principal of vectorial sum calculation of 3 phases.
In case of Earth Fault, the internal current sensor which makes the vectorial sum, detects the Earth Current and gives a tripping order according to Ig (Earth Fault Current) and tg (Tripping time for Earth Fault) settings.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!