15696 is replaced by:
Main range of productMulti 9 product nameMulti 9 PF product or component typeSurge arrester device short namePF8 device applicationDistribution poles description3P + N remote signallingWithout surge arrester typeElectrical distribution network earthing systemTN-STT [Uoc] open circuit voltage10 kV type 3 common mode N/PE10 kV type 3 differential mode L/N Complementary surge arrester class typeType 2 + 3 surge arrester technologyMOV + GDT [Ue] rated operational voltage230 V (+/- 10 %) AC 50/60 Hz400 V (+/- 10 %) AC 50/60 Hz [In] nominal discharge currentCommon mode : 2.5 kA L/PECommon mode : 2.5 kA N/PEDifferential mode : 2.5 kA L/N [Imax] maximum discharge currentCommon mode : 8 kA L/PECommon mode : 8 kA N/PEDifferential mode : 8 kA L/N [Uc] maximum continuous operating voltageCommon mode : 260 V N/PECommon mode : 340 V L/PEDifferential mode : 340 V L/N [Up] voltage protection level1 kV type 2 differential mode L/N1.1 kV type 3 differential mode L/N1.2 kV type 3 common mode N/PE1.5 kV type 2 common mode N/PE disconnector device typeAssociated circuit breaker 20 A - Icu 10 kAAssociated circuit breaker 20 A - Icu 15 kAAssociated circuit breaker 20 A - Icu 25 kA local signallingLED color: green/red mounting modeClip-on mounting supportDIN rail 9 mm pitches8 height81.4 mm width72 mm depth69 mm product weight0.355 kg colourGrey ( RAL 7035 ) response time<= 25 ns connections - terminalsTunnel type terminal, downside 2.5...35 mm²Tunnel type terminal, upside 2.5...35 mm² tightening torque2.5 N.m Environment quality labelsNFKEMA-KEUROVE IP degree of protectionOn front face : IP40 conforming to IEC 60529On terminal : IP20 conforming to IEC 60529 IK degree of protectionIK03 conforming to IEC 62262 relative humidity5...90 % operating altitude2000 m ambient air temperature for operation-25...60 °C ambient air temperature for storage-40...85 °C Contractual warranty Warranty period18 months
Documents and DownloadsLanguage
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.